VIBRATORY COOLING/CONTROL VALVE REPLACEMENT - CONTINUED
Oil is very slippery. Immediately wipe up any spills. Failure to follow this warning may cause injury.
Use container to catch any hydraulic oil that may drain from system. Dispose of oil IAW local pol-
icy and ordinances. Ensure all spills are cleaned up.
Mark and tag two electrical connectors for installation purposes.
Disconnect two electrical connectors (1) from vibratory cooling/control valve (2).
Remove cable tie (3) that fastens electrical harness to bracket (4).
Cap and plug all lines and fittings to prevent any contaminants from entering the system.
Disconnect seven hose assemblies (5) from vibratory cooling/control valve (2).
Remove six bolts (6) securing vibratory cooling/control valve (2) to vibratory pump (7).
Use caution when handling heavy parts. Provide adequate support and use assistance during procedure.
Failure to follow this warning may cause injury.
Weight of vibration cooling/control valve is 62 lb (28 kg.)
With assistance, remove vibratory cooling/control valve and spacer (8).
Remove four O-rings (9) from spacer (8) and vibratory cooling/control valve (2). Discard O-rings.